Add or Change Point Type
Did you know that you can now use 10K Type II temperature sensors in addition to 10K Type III in CBAS? This means that if Type II sensors are in place when retrofitting controllers at a site, you don’t have to change them.
The use of Type II is limited to the LX line of controllers. You must have a CBAS19 version and LX firmware dated January 15, 2020 or later for this to work.