The Lyric Centre, located at 440 Louisiana Street in downtown Houston, recently became one of Computrols newest customers. The building is 26 stories tall and provides approximately 385,000 square feet of commercial office space.
The Computrols Houston branch kicked off the project in October of 2017, integrating to the existing Johnson Controls system. In addition to interfacing with the existing JCI, DDC equipment, a core Computrols infrastructure is being installed. This infrastructure consists of a new headend computer, software, and lifetime-warranty controllers to replace the existing NAEs. These new DDC controllers communicate to the existing JCI equipment via N2 and BACnet protocols, enabling the building staff to monitor and control the existing JCI equipment. Computrols will also be providing additional lifetime-warranty controllers for future pneumatic to DDC floor conversions. Continue reading HVAC Controls Project: Lyric Centre – Houston, TX
In my last article, I discussed static pressure control and variable air volume (VAV) systems. I mentioned that by modulating the leaving air temp from an air handling unit (AHU) we can promote energy efficiency while also having an effect on static pressure. This time, we’ll look into how AHU supply temp sets the stage for efficient VAV operations.
Typically, VAVs are equipped with a means of reheating the supply air provided by the corresponding AHU. Continue reading AHU Supply Temp Sets the Stage
Static pressure is a key ingredient in a successful Variable Air Volume (VAV) system. It ensures that air flow will be available to enable the VAVs in a system to achieve their designed Cubic Feet per Minute (CFM) at maximum demand. Simply put, the push of the air must be greater than the resistance to the flow or no air will circulate through the ducts. Typically the setpoint for static pressure is determined through the course of the testing, adjusting, and balancing (TAB) at the end of a job. Continue reading Static Pressure Control and VAV Operation
Energy and water conservation deliver a wide range of advantages, including cost-related benefits, ancillary savings, infrastructure improvements, reduced pollutant emissions, improved energy security, and, in some cases, increased productivity. Continue reading Energy Efficiency Measures for Winter
Computrols is further expanding its footprint in Tampa, FL by having been awarded the opportunity to provide a complete pneumatic to DDC controls retrofit at One Tampa City Center. Over the next several months, Computrols will be working to install a number of its controllers to improve HVAC control and energy efficiency in the 750,000 square foot Class A office tower.
Computrols will be retrofitting the Tampa City Center’s current pneumatic system with its state of the art DDC building automation system. This new system provides technology that will allow for a new level of temperature control to enhance tenant comfort while reducing energy consumption.
The upgrade is scheduled for completion in September of 2016. The updated components will include: Continue reading Computrols Building Automation Project: Tampa City Center